Mode DIN-02-08 PLUS eDIN 8x2A Dimmer (8 channels of 2 Amps - Maximum Module Load 10A)
The Plus Model is the upgraded firmware model
An eight circuit dimmer module rated at 500W per circuit for the control of resistive and inductive lighting loads with the facility to select dimming or switched only operation of any circuit. A custom designed housing provides reliable power handling in a compact format.
- 8 x 500W Dimmer Module (total 10A maximum)
- Compact 9M width DIN Rail Mounting Module
- Selectable dimming or switching operation
- Programmable circuit Cap and Cup levels
- M-BUS enabled
- Low Load Compatible
- Operates resistive and inductive loads including low voltage electronic transformers (leading edge compatible type only)
- Energy Saving Display
- Quiet operation
- Can be installed as part of a 17th Edition Compliant installation
- Complies with EC EMC and Low Voltage Directives
- CE compliant
- ISO9001 certified design and manufacturing facility
Modules may be used in a standalone mode with simplified functionality providing programmable scene setting or Impulse (ON/OFF/DIM) type control from a single keypad. Alternatively conventional momentary switches can be linked to a contact Input Module (DIN-INT-00-08) to provide Impulse control of up to eight lighting circuits using eDIN Dimmer Modules.
An on-board menu system provides simple setup of circuit functions, maximum and minimum dimming levels, circuit test facility and power percentage monitoring. eDIN Dimmer modules may also be used in conjunction with a Network Processor Module to provide flexible, adaptable control for small to medium scale projects.
All eDIN Modules are M-BUS enabled and can be used with other Mode Lighting systems. This allows the flexible and compact eDIN Modules to be combined with the highly configurable Evolution System making Mode Lighting products the perfect choice for any scale of project.
eDIN Modules must be installed within a suitable surface mount enclosure with integral DIN rail. Installation must be carried out by a qualified electrician in accordance with the National Wiring Regulations and other applicable regulations. Compliance to EC EMC and Low Voltage Directives may be invalidated if not used or installed according to the published specification. eDIN Modules must be earthed.
Modules contain no user servicable parts and should not be opened.